In Australia the Input voltage is defined as 230Vac -6%/+10%. This effectively means that the voltage range of these products are 216Vac - 253Vac or 240V +6%
Standby power for non-maintained/switched maintained emergency devices is measured when the light is off and the charger is in standby mode. For maintained emergency devices, standby power is measured when the light is on and the charger is in standby mode. Typically, charging occurs for the first 16 hours after the device is powered or after a battery discharge.
Working Temp Range
0 to 40 °C
DALI DT1 Emergency
Wireless (IEC62386-104) with DT1
Re-wireable terminal block (5 pin)
Emergency (EM suffix)
Replacement Battery Code
DALI Monitored (DT1)
IEC62386-104 (Wireless DT1)
DALI Monitored ~ Supports Emergency test and monitoring over DALI (IEC62386) with full compliance to IEC62386-202. IEC62386-104 ~ Supports wireless test and monitoring over IEC62386-104 using IEC62386-202.
Emergency Lumen Output
Emergency Output Power
Product Design Life
The product design life relates to the total product life which includes LEDs, drivers and the enclosure. This is different to the LED lifetime which only refers to the economical lifetime of the LEDs at which time the lumen output has dropped below the L Value. The product design life is calculated at the maximum ambient or working temperature of the product and takes into account the Daily Use.